July 13, 2015 The non-existence of 'protective gadgets' on feeders and inefficient 'frequency synchronising' mechanism of K-Electric were the major reasons behind the recurrent feeder tripping, which causes hours-long power breakdown in the ... Business Recorder, 1 month ago
K-Electric's management issued a detailed statement explaining the power outage that occurred in Karachi and parts of Sindh and Balochistan on the eve of 7th July. According to KEs statement, the first breakdown in Karachi occurred at around 9pm ...4 Traders, 1 month ago KE reinforces Consumer Commitment despite Breakdown of Transmission Line Financial Daily, 1 month ago KE apologises for unforeseen breakdown Daily Times, 1 month ago KE explains reasons behind power breakdown Business Recorder, 1 month ago
MULTAN (APP): Police arrested three people for not providing identification during a joint search operation here on Saturday. According to a press release issued by police here, the Pak Army and police conducted joint search operation in Cantt, ...Frontier Post, 2 months ago
on your WebpageAdd Widget >Get your members hooked!